Chemical Waste Tanks
Sizing methodology complies with: Illinois Department of Public Health, Section 890.520
Please set the drainage area.
(based on selected square footage)
If square footage of drainage area exceeds 131,000 ft2, please call or email Striem.
Please select a pipe size.
Please select a flow rate.
If anticipated flow rate exceeds 300 GPM, please call or email Striem.
Oil Separator Calculations
Oil Separator Sizing
6.0 CU. FT. For First 500 SQ. FT. of Drainage Area
1.0 CU. FT. For Each Additional 500 SQ. FT. of Drainage Area
CU. FT. Requirement
Sizing methodology complies with Illinois Department of Public Health, Section 890.520